You can view the full version and download it in PDF format.
Page 3 of 82
Slots and openings in the cabinet are provided for ventilation to
ensure reliable operation of the CAMCORDER and to protect it from
overheating. These openings must not be blocked or covered.
Never place your CAMCORDER on a bed, sofa, rug, or other similar
surface: on or near a radiator or heat register.
This CAMCORDER should not be placed in a built-in installation such
as a bookcase or rack unless proper ventilation is provided or the
manufacturer’s instructions have been adhered to.
10. POWER SOURCES:
The CAMCORDER should be operated only from the type of power
source indicated on the label.
If you are not sure of the type of power supply at your home, consult
your appliance dealer or local power company.
A CAMCORDER is intended to be operated from battery power, or
other sources, refer to the operating instructions.
11. GROUNDING OR POLARIZATION:
This CAMCORDER may be equipped with either a polarized 2-wire
AC line plug (a plug having one blade wider than the other) or a 3-wire
grounding type plug, a plug having a third (grounding) pin.
If you are unable to insert the plug fully into the outlet, try reversing the
plug. If the plug still fails to fit, contact your electrician to replace your
outlet. Do not defeat the safety purpose of the polarized plug.
12. POWER-CORD PROTECTION:
Power-supply cords should be routed so that they are not likely to be
walked on or pinched by items placed upon or against them, paying
particular attention to cords or plugs, convenient receptacles,
point where they exit from the unit.
13. OUTDOOR ANTENNA GROUNDING:
If an outside antenna or cable system is connected to the
CAMCORDER, be sure the antenna or cable system is grounded to
provide some protection against voltage surges and built-up static
charges, Section 810 of the National Electrical Code, ANSI/NFPA No.
70-1984, provides information with respect to proper grounding of the
mast and supporting structure, grounding of the lead-in wire and
supporting structure, grounding of the mast and supporting structure,
grounding of the lead-in wire to an
antenna discharge unit, size of grounding to conductors, location of
antenna-discharge unit, connection to grounding electrodes and
requirements for the grounding electrode.
See figure below.
(NEC SECTION 810-21)
POWER SERVICE GROUNDING
(NEC ART 250, PART H)
NEC NATIONAL ELECTRICAL CODE
(NEC SECTION 810-20)
Notices and Safety Instructions